This page provides code information for mechanical systems and installations. The prevailing Code for mechanical installations is the Florida Building Code, Mechanical.
All permitted work shall be inspected. Inspections may be requested by permit holders online via the permitting portal or by calling (866) 957-3764, Option 5.
The information below is an overview of most commonly missed items during Residential inspections but is not an all-inclusive list.
FBC (R M) 1602.2 Note 4
Return air shall not be taken from a closest, mechanical room, or furnace room.
FBC (M) 505.1
Domestic kitchen exhaust shall be smooth inner walls.
FBC (Energy) R403.3.2
Mechanical Closest Sealing mandatory constructed and sealed in accordance with section C403.2.9.2 All joints between air barriers of walls, ceiling, floor, and door framing as well as all penetrations of air barriers shall be sealed to form airtight passageway.
FBC (R M) 1601.4.4
Support field, shop metal, and flex duct shall be supported to SMACNA HVAC standards.
FBC (RES) M1601.6
Furnace supply air to living space cannot supply to garage.
FBC (R) M1411.7
Refrigerant pipe within 1.5” of roof deck shall be protected
FBC (RES) R318
Cannot have expanding foam within 6” of the ground “terminate protection”.
FBC (Energy Table) R402.4.1.1 and R403.3.2
Require the mandatory sealing of all ducts, filter boxes, air handlers, and building cavities.
FBC (Energy) R403.4
Pipes/ condensate must be insulated when they carry any liquid under 55 or over 105
Light switch at opening and by appliance in attic.
FBC (R) 1602.3
Balanced return air need transfer and 1” undercut.
FBC (Mech) 406
Uninhabited spaces (crawl space attic) must have natural or mechanical ventilation.
FBC (R) (Table M) 1506.2
Shows need 4” flex on fans unless pipe 3” is used and max is 5 feet.
Manufactures such as Amana, Whirlpool, Maytag, etc., require dryer vent to terminate 12” above ground.
FBC (M) 603.9 181b
Tape on flex. 181 a-h for heat sensitive.
FBC (M) Table 401.5
Vent on residential .25” minimum; 0.5” max screen size.
FBC (M) 802.8
Insulation shield passing thru an insulated assembly.
FBC (R) 318.5
Condensate outside of homes 12”.
FBC (Energy Con) (R) 403.6
Outdoor air and exhaust have automatic damper or gravity damper.
FBC (M) 302.3.2
Stud notching 25% exterior and 40% nonbearing wall.